Thanks Gary and Mike. Gosh, that was fast work this morning! The pilot light went out because of something wrong with the thermal coupler (sp). The thermal coupler was changed out along with the wire which comes with it...I don't know...but it's working great again.
I'd bet 9 times out of 10 if you have a furnace pilot light as opposed to an igniter system, if the furnace stops running it's probably something to do with the pilot light.